The IP network fire alarm panel DI-9700FA is interface of fire alarm system and IP network PA system, which is used to receive 16 separate control input to trigger the IP network PA system auto broadcast multiple pre-recorded Alert or EVAC or Clear messages during emergency evacuation.
The IP network fire alarm panel DI-9700FA is interface of fire alarm system and IP network PA system, which is used to receive 16 separate control input to trigger the IP network PA system auto broadcast multiple pre-recorded Alert or EVAC or Clear messages during emergency evacuation. 19” rack mount design for universal rack installation, each zone with visualized indicator for status display, built-in IP network audio decoder to decode analog audio into digital via Ethernet. The pre-recorded messages stored in the IP network audio server which could be pre-assigned to different zones of different messages. Each fire alarm panel is of 32 zones, which could expandable of 40 units up to 6,000 speaker zones. The IP voice alarm or IP evacuation system panel could be built-up over existing LAN network, non-dedicated network is needed, so easy cable wiring and easy expansion and online trouble shoot and remote status monitoring make the system very popular for system contractors.
Interface between fire alarm and IP network audio system.
Automatically broadcast the pre-recorded message once triggered by the control input from the fire alarm center.
Different zone trigger could be assigned with different voice messages.
The multiple pre-recorded voice messages are stored in the server or controller.
The fire alarm center sends the fire alarm closed contact to this fire alarm panel, which will communicate with the server via the RJ45 port, the server will give command to generate which pre-set voice message to be broadcasted to pre-set speaker zone.
32 control inputs and 32 programmable control outputs.
The fire alarm panel capable for both IP network PA and intercom system.
Each IP PA system supports more than 40 units working together for more than 6,000 speaker zones.
IP voice alarm system could be built-up over existing LAN network, non-dedicated network is needed.
|IP Network Fire Alarm Panel
|AC220V or 240V, 50-60Hz
|TCP, UDP, ARP, ICMP, IGMP
|8KHz-48KHz, 16 bits
|8Kbps to 320Kbps
|One RJ45 port for LAN, 32 contact inputs and 32 contact outputs